Water Management in Process Plants. David A. Puckett University of Oklahoma Department of Chemical, Biological, and Materials Engineering 5/2/2008


 Tyrone Wilson
 3 years ago
 Views:
Transcription
1 Water Management in Process Plants David A. Puckett University of Oklahoma Department of Chemical, Biological, and Materials Engineering 5/2/2008
2 Abstract One of the primary weaknesses in currently used methods of optimizing water use and reuse in process plants is a lack of accurate modeling of water regeneration operating and capital costs. Both the operating and capital costs of water regeneration processes are generally taken as functions solely of treated water flow rate. However, the results of this assumption do not resemble the observed operating and capital costs trends for many water regeneration processes. The focus of this study was to use physical models of several commonly used water regeneration processes in order to generate general cost curves for these processes suitable for use in water use optimizations. As a result, general curves for process outlet concentration, process equipment cost, and process operating cost for the API separation, activated carbon adsorption, reverse osmosis, and Chevron wastewater treatment processes were generated. 1
3 Executive Summary In the interests of improving water use optimization model accuracy, physical models of several common processes commonly used in refineries for wastewater regeneration were developed. Specifically, the water regeneration processes modeled were: API separation Activated carbon adsorption Reverse osmosis Chevron wastewater treatment Once physical models for each of these processes were developed, the physical models were used to generate performance data for iterations of each of the processes as the process design variables were altered. Nonlinear regression when then used to develop relations between the design variables and the performance of the water regeneration process. Specifically, relations for the following performance aspects were developed. Process outlet concentration Process equipment cost Process operating cost For each of the processes modeled, the results were as follows: API separation o o o Activated carbon adsorption o o o Reverse osmosis o o o o o 2
4 Chevron wastewater treatment o o o o 3
5 Table of Contents Abstract... 1 Executive Summary... 2 Introduction... 5 API Separation... 7 Activated Carbon Adsorption... 8 Reverse Osmosis... 8 Chevron Wastewater Treatment... 9 Simulation Methods API Separation Activated Carbon Adsorption Reverse Osmosis Chevron Wastewater Treatment Equipment Cost Estimations Operating Cost Estimations Results Outlet Concentration Curves Equipment and Operating Cost Curves Recommendations Works Cited Appendices API Separation Activated Carbon Adsorption Reverse Osmosis Chevron Wastewater Treatment
6 Introduction Many of the process units used in the refining of crude oil taint process water with various contaminants. These contaminants vary from suspended organics to soluble organics, gases, and salts. This contamination forms the primary constraint on the efficient use of process water. It is always more profitable to use the wastewater from one process as the feed water of another process. However, the various process units each have maximum inlet contaminant concentrations at which they will function as designed. Therefore, wastewater regeneration may be necessary before wastewater reuse is possible. Process Contaminant Cin,max Cout,max Mass Load (ppm) (ppm) (kg/h) (1) Caustic Treating (2) Distillation (3) Amine Sweetening (4) Merox I Sweetening (5) Hydrotreating (6) Desalter Salts Organics H 2 S Ammonia Salts Organics H 2 S Ammonia Salts Organics H 2 S Ammonia Salts Organics H 2 S Ammonia Salts Organics H 2 S Ammonia Salts Organics H 2 S Ammonia Table 1: Maximum contaminant loads for refinery processes,(arnold & Samuel, 2007) 5
7 Various methods of removing contamination from wastewater are used in industry. For the contaminants most commonly encountered in refinery processes, (salts, organics, hydrogen sulfide, and ammonia), some commonly used wastewater treatment processes are as follows. Reverse osmosis to remove saline contamination API separation and activated carbon adsorption to remove organic contamination Chevron wastewater treatment to remove hydrogen sulfide and ammonia The methods currently used to optimize process water use and regeneration networks make several simplifying assumptions. Primary among these simplifications is the assumption that all costs associated with regeneration are functions solely of the treated wastewater flow rate. It is further assumed that the outlet concentrations of any regeneration process are fixed. However, these assumptions may not be accurate for both operating and capital costs for all wastewater regeneration processes. In particular, it should be noted that two wastewater regeneration systems that process the same amount of wastewater would have the same operating and capital costs regardless of whether one regeneration system was handling very concentrated waste whereas the other system was handling very dilute waste. This trend of constant cost regardless of separation quality is not the trend that would be predicted for most separation processes. Furthermore, consider the situation of two different separation processes, for instance an activated carbon adsorber and a distillation tower, that handle the same flow rate and the same contaminant. Under the simplifying assumptions used in current water use network optimization methods, both the API separator and the distillation tower would have the same operating and capital costs. Obviously this simplifying assumption produces results far from those that would be observed in practice. Therefore, there is a need to develop relations for the outlet concentrations, capital costs, and operating costs for various wastewater regeneration processes in order to remove the 6
8 inaccuracies introduced into water use optimization problems through the use of simplifying assumptions. In this study, several wastewater regeneration processes were analyzed with the intent of developing relations between system design variables and the process outlet concentration, equipment cost, and operating cost. The processes so analyzed were the treatment processes used most often in refineries: API separation, activated carbon adsorption, reverse osmosis, and the Chevron wastewater treatment process. The specifics of each of these treatment options are as follows. API Separation Figure 1: Schematic of an API separator The API separator works through the specific gravity differences present when water contaminants form a separate phase in water. Contamination will settle to the top or bottom of the separator as it travels through the separator in a stream of wastewater. For a given length and construction of API separator operating at a given flow rate, the quality of separation achieved will be a function solely of the specific gravity and diameter of the contaminant particles. In a refinery, an API separator will be used primarily to remove relatively large diameter (> 150 microns) particles of insoluble organic contaminants. 7
9 Activated Carbon Adsorption Figure 2: Activated carbon adsorption The activated carbon adsorber works through a contaminant being more soluble on the surface of an activated carbon particle than in water. Thus, the contaminant will partition favorably in the activated carbon relative to water. For an activated carbon adsorption system that reaches the solubility limit of the activated carbon, the quality of separation achieved will be determined solely by the adsorption thermodynamics, not by the construction of the adsorber. In a refinery, activated carbon adsorption will be used primarily in the removal of soluble and emulsified organics, i.e. organics that cannot be removed via an API separator. Reverse Osmosis Figure 3: Schematic of a reverse osmosis process 8
10 A reverse osmosis separation process works by using external pressure to overcome an osmotic pressure gradient across a membrane selectively permeable to water. For all reverse osmosis systems, the quality of separation achieved is a function solely of the properties of the membrane. Design variables such as membrane thickness and external pressure will only alter the amount of water the reverse osmosis system can process in a given time. In a refinery, reverse osmosis separation process will be used primarily to remove dissolved salts from process water. Chevron Wastewater Treatment Partial Condenser Hydrogen Sulfide Stream Ammonia Stream Hydrogen Sulfide Stripper Water feed Ammonia Stripper Partial Reboiler Partial Reboiler Stripped water Chevron Waste Water Treatment PFD Figure 4: PFD of the Chevron wastewater treatment process The Chevron wastewater treatment process consists of stripping column for the removal of hydrogen sulfide in series with a refluxed distillation column for the removal of ammonia. The Chevron wastewater treatment process works through the high volatilities of hydrogen sulfide and ammonia relative to water. By heating a solution of hydrogen sulfide and ammonia in water, a vapor will be produced that will be enriched for hydrogen sulfide and ammonia relative to the original solution. The quality of separation achieved by the Chevron wastewater treatment process is very much dependent on the design variables chosen in the production of the system, especially tray efficiency and tray 9
11 number. In a refinery, the Chevron wastewater treatment system will be used solely for the removal of hydrogen sulfide and ammonia from process water although the basic system is suitable for the removal of any contaminant of suitably high volatility. Simulation Methods The method used to develop relations between water regeneration system design variables and the outlet concentrations, equipment costs, and operating costs for the various water regeneration processes is simple in concept but involved in application. Each of the water regeneration processes has one or several fundamental design equations. Using these design equations, the performance and cost of a range of process designs can be modeled. Through nonlinear regression, the results of these models can be combined into three fundamental equations; one equation relating outlet concentration to design variables, one equation relating equipment cost to design variables, and one equation relating operating cost to design variables. For each of the water treatment processes modeled, the fundamental design equations used are as follows. API Separation API type separators are used to remove waste water contaminants that are insoluble in water such as sediment, oil, and various insoluble organics. As the contaminants are insoluble, the contaminants will form a separate phase that will settle to either the top or the bottom of the separator based on Stokes Law: Equation 1 V S 2 9 r 2 g p p p f 10
12 Where, V s is the settling velocity of the particle, r is the Stokes radius of the particle, g is the gravitational acceleration coefficient, p p is the density of the particle, p f is the density of the fluid, and μ is the viscosity of the fluid the particle is settling through. As there is flow through the separator while the contaminants are settling, the contaminant particles will have a forward velocity independent of their settling velocity based on the flow rate through the separator. As the API separator specification requires that the separator geometry be such that there is bulk flow through the separator, the horizontal velocity of each contaminant particle should be the bulk velocity of the flow through the separator, (the separator flow rate divided by separator cross sectional area). Using the below equation and Stokes Law, the minimum particle diameter that will settle can be determined through substitution. Equation 2 H V s s L V x x Where H s is the settling distance, V s is the settling velocity of the particle as given in equation 1, L x is the length of separator, and V x is the bulk velocity of flow through the separator. Any particle larger than the minimum particle size as calculated above will settle in the separator. If a normal distribution is assumed for the contaminant particle diameters and the actual contaminant particle diameter is equal to the Stokes diameter of the particle (i.e. the particles are spherical), the proportion of the contaminant that will settle out in the API separator can be calculated using the following equation: 11
13 Equation 3 r min r r e e r R 2 r R dr dr Where rmin is the minimum particle radius that will settle, r is the particle radius, σ is the standard deviation of the normal particle distribution, and R is the mean particle radius. It should be noted that 1 2 e r 2 R 2 2 is the Gaussian probability density function, so the above equation is simply the integral of the volume of any given particle multiplied by the probability of a random particle being of that volume for the particles that settle divided by the same integral for all particles. Activated Carbon Adsorption Removal of a contaminant through adsorption onto activated carbon is modeled by assuming that the limiting factor in mass transfer is pore diffusion, as should be the case with activated carbon of sufficiently high surface area to volume ratio in a nonstagnant fluid. For the pore diffusion limiting case, the following equation should describe the rate of change in contaminant concentration within a spherical activated carbon particle: C t D I P PI 2 P P dn dc I I r 2 r r C r I Equation 4 12
14 Where C I is the bulk contaminant concentration, N I is the amount of contaminant adsorbed onto activated carbon, t is time, r is the radial position within the activated carbon particle, ε p is the porosity of the activated carbon particle, ρ p is the activated carbon particle density, and D PI is the diffusivity of the contaminant in the pores of the adsorbent particle(perry & Green, 1997). For calculating the amount of contaminant adsorbed at equilibrium, the Langmuir adsorption isotherm was used. Equation 5 N I 1 N IS K ICI K ICI Where N I is the amount of contaminant adsorbed at equilibrium weight of adsorbent, N IS is the number of adsorbing sites per weight of adsorbent, K I is the equilibrium constant for the adsorption, and C I is the bulk contaminant concentration. The solution for the rate of adsorption was found using the linear driving force approximation of the adsorption system adjusted for the pore diffusion limited case as given below: Equation 6 N t I k R N IS ( R CI CIF C 1) C I IF N I Equation 7 k 15 1 r 2 p p D Ip 13
15 Equation R Equation 9 D Ip D I Equation 10 1 b 1 b 1 p Equation 11 1 p p 1 1 s p Equation 12 r p 2 A p p Equation 13 bn C IF IS Equation 14 1 R 1 K I C IF 14
16 Where ρ b is bulk density of adsorbent, ρ p is particle density of adsorbent, ρ s is density of adsorbent skeleton, A is surface area per weight of adsorbent, K I is Langmuir equilibrium coefficient, C I is bulk concentration of contaminant, C IF is feed concentration of contaminant, N I is amount of contaminant adsorbed per weight of adsorbent, N IS is the number of adsorption sites per weight of adsorbent, N I is the mean amount of contaminant adsorbed in a unit of adsorbent, D I is the diffusivity for the contaminant in the working fluid, τ is the tortuosity of the adsorbent particle, R is the separation factor, r p is the mean pore diameter for the adsorbent particle, Λ is the partition ratio, ε p is the void fraction in the adsorbent particle, ε is the packing void fraction in the bulk adsorbent, D Ip is the diffusivity for the contaminant in the pores of the adsorbent, Ψ is the correction factor for pore transfer under the linear driving force assumption, k is the linear driving force rate constant, and t is time(perry & Green, 1997). Reverse Osmosis Removal of salt through reverse osmosis is modeled through a modification of Fick s first law of diffusion to account for diffusion through a semipermeable membrane. Equation 15 N p w z P Where N is the water flux through the membrane, p w is the permeability of the membrane with respect to water, z is the thickness of the membrane, ΔP is the pressure gradient across the membrane, and ΔΠ is the osmotic pressure gradient across the membrane. The osmotic pressure is determined through the van t Hoff approximation of osmotic pressure: crt Equation 16 15
17 Where Π is the osmotic pressure, c is the total concentration of ions, R is the gas constant, and T is the absolute temperature. It should be noted that the van t Hoff approximation is not especially accurate for very concentrated brines. The concentration of ions on the purified water side of the membrane is determined using the rejection ratio for the particular salt that is being removed (a property of the membrane that should be specified by the membrane manufacturer). The amount of rejected salt is similarly calculated from the rejection ratio. If multiple salts are present in significant concentrations, a weighted average rejection ratio can be used. Once the flux through the membrane is determined, the flow rate of water through the reverse osmosis unit can be easily determined through multiplication of the flux and the membrane area. Chevron Wastewater Treatment Both the hydrogen sulfide stripper and the ammonia distillation unit in the Chevron wastewater treatment process were simulated using the McCabeThiele method taken analytically. An outlet concentration for the waste vapor from both units was assumed in order to provide a starting point for the McCabeThiele operating lines. Ideal liquid and vapor mixtures were assumed in obtaining the vapor liquid equilibrium lines. At the reasonably elevated temperatures, and low pressures that the stripping and distillation towers are expected to run at, the system should be close to ideal. For determining the wastewater flow rate through the process, the following relationship to vapor flow rate at flooding was used, with the Souders and Brown factor being approximated from charts in (Peters, Timmerhaus, & and West, 2002): Equation L V VV CSB % 20 V F V F A LRA 16
18 Where V V is the vapor velocity in m/s, C SB is the Sauders and Brown factor in m/s, σ is the surface tension of the liquid in dynes/cm, ρ L is the liquid density, ρ V is the vapor density, % F is the percent of flooding at which the stripping tower or distillation tower is operated, V F is the vapor volumetric flow rate, A is the crosssectional area of the stripping or distillation tower, L is the rate of liquid entry into the reboiler, and R is the fraction of liquid boiled in the reboiler. Equipment Cost Estimations A power law relation between capacity and equipment cost is available for the pricing the pumps necessary for a wastewater regeneration system(perry & Green, 1997). Equation 18 Where EC is the equipment cost for the pump and P is the power of the pump in kilowatts. The required pump power can be calculated through the following equation (Perry & Green, 1997): Equation 19 Where P is the pump power in kilowatts, H is the dynamic head for the system in meters, Q is the capacity of the pump in cubic meters per hour, ρ is the density of the liquid being pumped, and η is the pump efficiency. For all pumps, an efficiency of 75% was assumed for all power calculations. While power law relations for equipment cost are available for pricing pumps, the same is not true for pricing the main portions of the most of the separation units. Specifically, relations between the equipment costs of API separators, reverse osmosis units, and activated carbon adsorbers had to be developed from whole cloth. For this study, it was assumed that raw materials would form 67% of the 17
19 cost of all separators. Furthermore, it was assumed that the casings for all API separators, reverse osmosis units, and activated carbon adsorbers modeled would be composed of 1 cm thick 1020 carbon steel. Based on this thickness, the density of carbon steel, and the measurements of the treatment units modeled, the mass of steel required for each treatment unit can be calculated. The same manner of process can be used for determining the amount of activated carbon initially required for the activated carbon adsorbers. For the reverse osmosis units, it was assumed that cellulose triacetate would be the material used in the construction of the membrane. Membrane specific price was further assumed to be independent of membrane thickness. Based on the quantities of raw materials required, the cost of raw materials was calculated using the following prices. Price of 1020 carbon steel: $833 per ton Price of activated carbon: $2300 per ton Price of cellulose triacetate: $90 per square meter It should be noted that these prices were only used in obtaining the initial data used in developing equipment cost relations. The equipment cost relations themselves provide an adjustment factor for the actual price of the raw materials in question. The equipment costs for the stripping and distillation columns required for the Chevron wastewater treatment process were priced by fitting lines to charts provided in (Peters, Timmerhaus, & and West, 2002). Briefly stated, the equipment cost for a stripping or distillation column is taken to be a factor of column diameter and the number of trays present in the column as well as the material used in the construction of the column. For the purposes of this study, it was assumed that all columns would be constructed completely out of stainless steel. As the Chevron wastewater treatment process is used for the removal of corrosive gas components from water, it is reasonable to assume that stainless steel would be used in the construction of the requisite columns in order to reduce the risk of corrosion. 18
20 While a price for stainless steel was not required to use the charts in (Peters, Timmerhaus, & and West, 2002), a price for stainless steel at the time the charts were generated is be necessary for adjusting the results obtained from the charts to current stainless steel prices. For the purpose of adjustment, the following price for stainless steel in 2002 was used. Price of stainless steel: $1400 per ton Operating Cost Estimations For all of the water treatment processes modeled, a significant operating cost for the process is the cost of pumping the water to be treated through the treatment process. For an API separator or a reverse osmosis unit, the cost of pumping amounts to the primary operating cost. For the refluxed distillation tower used in the Chevron wastewater treatment process, additional pumping costs come from the requirement for cooling water in the column condenser. As the pumping power required for each system has already been calculated for the sizing of the pump required for the system, the operating cost for pumping is found through the application of the price of electrical power. For the purposes of this study, a price of $0.07 per kilowatthour was assumed for all operating cost calculations. However, in a similar fashion to the raw materials prices, a factor was provided in all obtained operating cost relations to adjust the operating cost to the current price of electricity. For the activated carbon adsorbers, an additional operating cost above the cost of pumping water through the system consists of regenerating the activated carbon used in the adsorption. The cost of regenerating the activated carbon was assumed to be 65% of the cost of obtaining virgin activated carbon with an additional 15% of the cost of obtaining virgin activated carbon added on to represent the losses of activated carbon in the regeneration process. These assumptions regarding the cost of regenerating the activated carbon would be reasonably accurate if the activated carbon used in the adsorber were regenerated offsite. If regeneration were performed onsite, savings may be 19
21 possible if significant enough quantities of activated carbon were being regenerated. Similarly to all of the other costs associated with the regeneration processes, a correction factor was provided to account for activated carbon regeneration cost savings. For the stripping and distillation columns used in the Chevron wastewater treatment process, reboiler heat duty presented an additional operating cost above pumping requirements. For both of the column types, reboiler duty was calculated using the reboil ratio for the partial reboiler (the fraction of the liquid entering the reboiler that is boiled) and the heat capacity and heat of vaporization of water. For the likely percentage of hydrogen sulfide and ammonia present in the water being treated in the Chevron wastewater treatment process, the contribution of hydrogen sulfide and ammonia to the heat capacity and heat of vaporization of the wastewater was assumed to be negligible. Similarly, the effect of mixture nonidealities on the heat duty of the reboiler was also assumed to be of negligible importance. For providing the heat to the reboiler, it was assumed that the fundamental source of the heat would be combustion of natural gas with 85% of the lower heating value of the gas being available for heating the column. A price of $7.33 per MMBTU was assumed the cost of natural gas. Similarly to all of the other costs, a correction factor for differing prices of heat was provided. Results Using the modeling equations and assumptions stated previously, the outlet concentrations, equipment costs, and operating costs for the four water treatment processes analyzed were obtained with varying design parameters. Nonlinear regression was used to fit multivariable curves to the data so generated. 20
22 Outlet Concentration Curves For all of the water treatment methods analyzed in this study, the outlet concentration of the treatment process can be calculated directly from the design equations for the process. However, for several water treatment methods, specifically API separation and the Chevron wastewater treatment method, the exact calculation method is cumbersome to use in water use optimizations. To simplify the implementation of the outlet concentration curves in water use optimizations, it is possible to express the exact solutions for outlet concentration as a combination of nonlinear functions through the use of regression. The regression option was chosen for use with the outlet concentrations of the API separation process, where outlet concentration is determined through an integral that can only be evaluated numerically, and the Chevron wastewater treatment process, where outlet concentration is the product of a system of equations, in order to simplify equation implementation. API Separation The outlet concentration of an API separator can be calculated exactly, if a normal distribution of particle diameters is assumed and the particles are uniformly spherical, through the application of Stokes Law and the following solution to equation 3. Equation 20 Equation 21 21
23 Where r min is the minimum radius of particle that will settle in the API separator as given by Stokes Law, R is the mean particle radius, σ is the standard deviation in the particle size distribution, C OUT is the outlet concentration to the separator, and C IN is the inlet concentration to the separator. In the interests of easy implementation of this simulation of the API separator in a water use optimization, the following regression for the dependence of the outlet concentration of an API separator on the design parameters of the separator was performed. Figure 5: Nonlinear regression for API separator outlet concentration It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the objective function achieved at the combination of variables the data point references (in the case of an API separator, the percentage of contaminants removed). The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. Through data point 8, settling 22
24 distance was varied. From data point 9 to data point 13, separator length was varied. From data point 14 to data point 21, the difference in specific gravity between the contaminant and water was varied. From data point 22 to data point 26, contaminant mean particle diameter was varied. From data point 27 on, the wastewater velocity was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From this regression, the following relation between the design variables for the API separator and the percentage of contamination removed was developed. Equation 22 Where h is the settling distance in meters, L is the separator length in meters, ΔSG is the difference in specific gravity between the contaminant and water, D p is the mean contaminant particle diameter in millimeters, F is the volumetric flow rate through the separator in cubic meters per second, and A is the cross sectional area of the separator in square meters. Equation 21 can then be used to take the percentage of contamination removed and generate the outlet concentration. As figure 5 indicates, the regression should prove reasonably accurate for variations in most of the design variables for the API separator. However, a more transcendental dependence of the percentage of contamination removed on settling distance may result in a better fit overall. Activated Carbon Adsorption The outlet concentration of an activated carbon adsorber can be calculated easily and simply from the Langmuir adsorption isotherm if the adsorber reaches equilibrium with the feed to the adsorber. 23
25 Equation 23 Where K is the Langmuir adsorption coefficient, C OUT is the outlet concentration of the adsorber, and C IN is the inlet concentration of the adsorber. Reverse Osmosis The outlet concentration of a reverse osmosis unit can be calculated easily and simply from the design parameters of the unit as follows. Equation 24 Where RP is the rejection percentage of the membrane for the contaminant in question, N is the number of membranes connected in series, C OUT is the outlet concentration of the reverse osmosis unit, and C IN is the inlet concentration of the reverse osmosis unit. Chevron Wastewater Treatment Similarly to the case of the API separator, regressions were used to develop general relations between outlet concentration and the design variables for the columns used in the Chevron wastewater treatment process. The curve obtained for the hydrogen sulfide stripping column is as follows. 24
26 Figure 6: Nonlinear regression for hydrogen sulfide stripping column outlet concentration It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the objective function achieved at the combination of variables the data point references (in the case of a hydrogen sulfide stripper, the outlet mole fraction of contamination). The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. Through data point 12, tray number was varied. From data point 13 to data point 20, inlet mole fraction of contaminant was varied. From data point 21 to data point 28, the reboil ratio was varied. From data point 29 on, mean tray efficiency was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From this regression, the following relation between the design variables for the hydrogen sulfide stripper and the outlet mole fraction of contamination was developed. 25
27 Equation 25 Where TN is the number of trays in the column, RBR is the reboil ratio, η is the mean tray efficiency, X OUT is the mole fraction of contaminant at the outlet of the column, and X IN is the mole fraction of contaminant at the inlet to the column. A similar regression can be performed for the refluxed distillation column used for ammonia removal. Figure 7: Nonlinear regression for ammonia distillation column outlet concentration It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the objective function achieved at the combination of variables the data point references (in the case of a ammonia distillation column, the outlet mole fraction of contamination). The various peaks in the graph were generated by a 26
28 single variable being varied while all other variables were held constant. Through data point 10, tray number was varied. From data point 11 to data point 18, inlet mole fraction of contaminant was varied. From data point 19 to data point 25, the reflux ratio was varied. From data point 26 to data point 32, reboil ratio was varied. From data point 33 on, mean tray efficiency was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From this regression, the following relation between the design variables for the hydrogen sulfide stripper and the outlet mole fraction of contamination was developed. Equation 26 Where TN is the number of trays in the column, RBR is the reboil ratio, RFR is the reflux ratio, η is the mean tray efficiency, X OUT is the mole fraction of contaminant at the outlet of the column, and X IN is the mole fraction of contaminant at the inlet to the column. It should be noted that the regression does show some deviation from the predicted data at low reflux ratios close to the minimum reflux ratio for the column due to the requirement for an infinite column height at minimum reflux. Equipment and Operating Cost Curves For all of the water treatment methods analyzed in this study, relations for equipment cost and operating cost were obtained as combinations of transcendental functions through nonlinear regression. Exact solutions for the equipment cost and operating cost of each of the water treatment methods analyzed are possible, but the use of regression was chosen for ease of implementation. If fixed capital investment relations are required instead of equipment cost relations, the equipment cost curves obtained for each of the water treatment methods can be multiplied by a constant Lang factor. API Separation The following regression was performed for the equipment cost for an API separator. 27
29 Figure 8: Nonlinear regression for the equipment cost for an API separator It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the equipment cost achieved at the combination of variables the data point. The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. Through data point 45, the quality of separation achieved in the API separator was varied in steps over a range of flow rates. From data point 46 to data point 51, the difference in specific gravity between the contaminant and water was varied. From data point 52 to data point 56, the mean contaminant particle diameter was varied. From data point 57 on, the settling height for the separator was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From the same variables, the following regression for the operating cost of an API separator was performed. 28
30 Figure 9: Nonlinear regression for the operating cost for an API separator From these regressions, the following relations between the design variables for the API separator and the equipment cost and operating cost of the separator were developed. Equation 27 Equation 28 Where F is the flow rate through the system in cubic meters per second, %QS is the percentage of contaminant removed, ΔSG is the difference in specific gravity between the contaminant and water, Dp is the mean contaminant particle diameter in millimeters, h is the settling height for the separator in meters, PST is the current price of steel in dollars per ton, PE is the current price of electricity in dollars 29
31 per kilowatthour, EC is the equipment cost for the separator, and OC is the operating cost of the separator. It should be noted that the regression for equipment cost breaks from the simulated results for separation qualities above 99.5% due to the length of the separator approaching infinity as the quality of separation approaches 100%. Activated Carbon Adsorption adsorber. The following regression was performed for the equipment cost for an activated carbon Figure 10: Nonlinear regression for the equipment cost for an activated carbon adsorber It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the equipment cost achieved at the combination of variables the data point. The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. Through data point 9, the 30
32 flow rate through the adsorber was varied. From data point 10 to data point 19, the contaminant concentration at the inlet to the adsorber was varied. From data point 20 to data point 25, the height of the adsorber was varied. From data point 26 on, the diameter of the adsorber was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From the same variables, the following regression for the operating cost of an activated carbon adsorber was performed. Figure 11: Nonlinear regression for the operating cost for an activated carbon adsorber From these regressions, the following relations between the design variables for the activated carbon adsorber and the equipment cost and operating cost of the adsorber were developed. Equation 29 31
33 Equation 30 Where F is the flow rate through the system in cubic meters per hour, C IN is contaminant concentration at the inlet to the adsorber in kilograms per cubic meter, D is the diameter of the adsorber in meters, H is the height of the adsorber in meters, PST is the current price of steel in dollars per ton, PAC is the current price of activated carbon in dollars per ton, PE is the current price of electricity in dollars per kilowatthour, PACR is the current price of activate carbon regeneration in dollars per ton, EC is the equipment cost for the adsorber, and OC is the operating cost of the adsorber. Reverse Osmosis The following regression was performed for the equipment cost of a reverse osmosis unit. Figure 12: Nonlinear regression for the equipment cost for a reverse osmosis unit 32
34 It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the equipment cost achieved at the combination of variables the data point. The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. For the whole of the data set used in the regression, the inlet concentration to the reverse osmosis unit was varied in steps over a range of flow rates. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From the same variables, the following regression for the operating cost of a reverse osmosis unit was performed. Figure 13: Linear regression for the operating cost for a reverse osmosis unit 33
35 From these regressions, the following relations between the design variables for the reverse osmosis unit and the equipment cost and operating cost of the unit were developed for single membranes and for membranes in series. Equation 31 Equation 32 Equation 33 Equation 34 Where F is the flow rate through the system in cubic meters per hour, C IN is contaminant concentration at the inlet to the adsorber in moles per cubic meter, BR is the bypass ratio for the membrane (the fraction of water that enters the inlet of the membrane unit that is retained), N is the number of membranes in series, PM is the current price of the membrane in dollars per square meter, PE is the current price of electricity in dollars per kilowatthour, EC is the equipment cost for the reverse osmosis unit for the case of a single membrane, ECs is the equipment cost for the reverse osmosis unit for the case of membranes in series, OC is the operating cost of the reverse osmosis unit for the case of a single 34
36 membrane, and OCs is the operating cost of the reverse osmosis unit for the case of membranes in series. Chevron Wastewater Treatment The equipment and operating costs for the stripping and distillation columns used in the Chevron wastewater treatment process both follow the same trends in equipment and operating cost. Thus, it is only necessary to perform regressions for equipment and operating cost for either the stripping column or the distillation column in order to develop relations that are appropriate for both types of column. The following regression was performed for the equipment cost of a stripping or distillation column. Figure 14: Nonlinear regression for the equipment cost for a stripping or distillation column It should be noted that since that since this is a multivariable regression, the axis of abscissas cannot reference any particular variable. Thus, the axis of abscissas is simply marked off with the number of the data point used in the regression whereas the axis of ordinates references the equipment cost 35
37 achieved at the combination of variables the data point. The various peaks in the graph were generated by a single variable being varied while all other variables were held constant. Through data point 7, the flow rate through the column was varied. From data point 8 to data point 11, the number of trays in the column was varied. From data point 12 on, the diameter of the column was varied. For the graphs, blue markers represent the simulation results whereas green markers represent the results of the regression. From the same variables, the following regression for the operating cost of a stripping or distillation column was performed. Figure 15: Linear regression for the operating cost for a stripping or distillation column From these regressions, the following relations between the design variables for a stripping or distillation column and the equipment cost and operating cost of the column were developed. Equation 35 36
38 Equation 36 Where F is the flow rate through the system in cubic meters per hour, TN is the number of trays in the column, D is the diameter of the column in meters, PSS is the current price of stainless steel in dollars per ton, PH is the current price of heat in dollars per MMBTU, EC is the equipment cost for the column, and OC is the operating cost of the column. Recommendations In order to develop water use optimization methods of greater accuracy than the methods currently used, a reduction in the use of simplifying assumptions is necessary. Specifically, the assumptions of fixed regeneration process outlet concentration and flow rate dependent costs introduce inaccuracies into water use optimization models. Through the direct substitution of the relations for process outlet concentration, process equipment cost, and process operating cost developed in this study for the assumed outlet concentrations and costs, these modeling inaccuracies can be rectified for some of the more common water regeneration methods. For water regeneration processes not covered in this study, a similar method of rectifying modeling inaccuracies as used in this study can be applied (i.e. a physical model of the process can be developed, the physical model can be used to generate performance data for a variety of process designs, and nonlinear regressions can be performed on this data to develop relations for process outlet concentration, equipment cost, and operating cost). Similarly, water contaminating processes could be modeled in the same manner to remove further sources of inaccuracy in water use optimization models. 37
39 Works Cited Arnold, M. C., & Samuel, J. (2007). Water Management in Refineries. Perry, R., & Green, D. (1997). Perry's Chemical Engineers' Handbook (7th ed.). McGrawHill. Peters, M., Timmerhaus, K., & and West, R. (2002). Plant Design and Economics for Chemical Engineers, 5th Edition. McGrawHill. 38
40 Appendices API Separation 39
41 40
42 41
43 Activated Carbon Adsorption 42
44 43
45 44
46 45
47 Reverse Osmosis 46
48 47
49 48
50 49
51 Chevron Wastewater Treatment 50
52 51
53 52
54 53
55 54
Water Management in Refining Processes
Water Management in Refining Processes Amy Frink Timilehin Kehinde Brian Sellers Department of Chemical, Biological, and Materials Engineering 5/8/009 Table of Contents Background... Simulation Methods...
More informationA DESIGN REVIEW OF STEAM STRIPPING COLUMNS FOR WASTEWATER SERVICE. Timothy M. Zygula. Huntsman Polymers 2504 South Grandview Ave Odessa, TX 79760
A DESIGN REVIEW OF STEAM STRIPPING COLUMNS FOR WASTEWATER SERVICE Paper 7A Timothy M. Zygula Huntsman Polymers 2504 South Grandview Ave Odessa, TX 79760 Prepared for Presentation at the The AIChE 2007
More informationIntroduction to Distillation. Binous  Introd. to Distillation
Introduction to Distillation 1 Exploits differences in boiling point, or volatility Requires the input of energy Handles a wide range of feed flow rates Separates a wide range of feed concentrations Produce
More informationNathan A. Hatcher and Ralph H. Weiland, Optimized Gas Treating Inc., USA, discuss the fate of ammonia in refinery amine systems.
Special treatment T he corrosion that results from ammonia ingress and accumulation in refinery and biogas amine systems is a problem that may be exacerbated by the increasing utilisation of advantaged
More informationIn 1965, while working as a
Sour strippers: design and operation Simpler, more costeffective sour stripper designs can outperform more generally accepted designs in the refining industry NORMAN LIEBERMAN Process Improvement Engineering
More informationFate of Ammonia in Refinery Amine Systems
Fate of Ammonia in Refinery Amine Systems Nathan A. Hatcher and Ralph H. Weiland Optimized Gas Treating, Inc. Sugar Land, TX INTRODUCTION Ammonia ingress and accumulation in refinery and biogas amine
More informationDesign of LiquidLiquid Extraction Columns Introduction LiquidLiquid Extraction Balances on LiquidLiquid Extraction...
Design of LiquidLiquid Extraction Columns All rights reserved, Armando B. Corripio, Ph.D., P.E., 2014 Cain Department of Chemical Engineering Corripio@LSU.edu Louisiana State University, Baton Rouge,
More informationMass Transfer Rate Modeling Basics. Nathan A. Hatcher, P.E. AIChE South Texas Section Dinner Pellazio Banquet Hall, Houston TX September 11, 2014
Mass Transfer Rate Modeling Basics Nathan A. Hatcher, P.E. AIChE South Texas Section Dinner Pellazio Banquet Hall, Houston TX September 11, 2014 Outline History of Process Simulation Briefly about the
More informationA Simple Application of Murphree Tray Efficiency to Separation Processes
Page 1 of 8 A Simple Application of Murphree Tray Efficiency to Separation Processes J.J. VASQUEZESPARRAGOZA, J.C. POLASEK, V.N. HERNANDEZVALENCIA, M.W. HLAVINKA, Bryan Research & Engineering, Inc.,
More informationModular Oil & Gas Equipment Onshore & Offshore
Modular Oil & Gas Equipment Onshore & Offshore Separators & Desalters AI Energy Solutions onshore and offshore oil process solutions offer innovative technologies packaged with global project management
More informationHYSYS WORKBOOK By: Eng. Ahmed Deyab Fares.
HYSYS WORKBOOK 2013 By: Eng. Ahmed Deyab Fares eng.a.deab@gmail.com adeyab@adeyab.com Mobile: 00201227549943  Email: adeyab@adeyab.com 1 Flash Separation We have a stream containing 15% ethane, 20% propane,
More informationWWT TwoStage Sour Water Stripping
WWT TwoStage Sour Water Stripping Improve performance of sulfur recovery units ben efits The Chevron WWT Process is a twostage stripping process which separates ammonia and hydrogen sulfide from sour
More informationGTLPG Max SM. Maximizing LPG Recovery from Fuel Gas Using a Dividing Wall Column. Engineered to Innovate
GTC Technology White Paper GTLPG Max SM Maximizing LPG Recovery from Fuel Using a Dividing Wall Column Engineered to Innovate GTLPG Max SM Maximizing LPG Recovery from Fuel Using a Dividing Wall Column
More informationReactors and Separations Design Project. Phthalic Anhydride Production
Reactors and Separations Design Project Phthalic Anhydride Production We are continuing our evaluation of process alternatives for the production of Phthalic Anhydride via the catalytic oxidation of oxylene.
More informationCOMSOL Multiphysics Simulation of Flow in a Radial Flow Fixed Bed Reactor (RFBR)
COMSOL Multiphysics Simulation of Flow in a Radial Flow Fixed Bed Reactor (RFBR) Anthony G. Dixon *,1, Dominic Polcari 1, Anthony Stolo 1 and Mai Tomida 1 1 Department of Chemical Engineering, Worcester
More informationSeparations and Reactors. Acrylic Acid Production via the Catalytic Partial Oxidation of Propylene
Separations and Reactors Acrylic Acid Production via the Catalytic Partial Oxidation of Propylene Process Information Background Acrylic acid (AA) is used as a precursor for a wide variety of chemicals
More informationFluid Mechanics, Heat Transfer, Thermodynamics Design Project. Production of Styrene
Fluid Mechanics, Heat Transfer, Thermodynamics Design Project Production of Styrene The feasibility of constructing a new, grassroots, 100,000 tonne/y, styrene plant is being investigated. As part of
More informationPOROSITY, SPECIFIC YIELD & SPECIFIC RETENTION. Physical properties of
POROSITY, SPECIFIC YIELD & SPECIFIC RETENTION Porosity is the the ratio of the voids to the total volume of an unconsolidated or consolidated material. Physical properties of n = porosity as a decimal
More informationENERGY EFFICIENT SYNTHESIS AND DESIGN FOR CARBON CAPTURE
Distillation Absorption 2010 A.B. de Haan, H. Kooijman and A. Górak (Editors) All rights reserved by authors as per DA2010 copyright notice ENERGY EFFICIENT SYNTHESIS AND DESIGN FOR CARBON CAPTURE Angelo
More informationEstimation of BoiloffGas BOG from Refrigerated Vessels in Liquefied Natural Gas Plant
International Journal of Engineering and Technology Volume 3 No. 1, January, 2013 Estimation of BoiloffGas BOG from Refrigerated Vessels in Liquefied Natural Gas Plant Wordu, A. A, Peterside, B Department
More informationMOLECULAR GATE TECHNOLOGY FOR (SMALLER SCALE) LNG PRETREATMENT
MOLECULAR GATE TECHNOLOGY FOR (SMALLER SCALE) LNG PRETREATMENT Presented at the 2010 Gas Processors 89 th Annual Convention Austin, TX March, 2010 Michael Mitariten, P.E. Guild Associates, Inc. Dublin,
More informationFluid Mechanics, Heat Transfer, Fluid Mechanics Design Project. Production of Ethanol
Fluid Mechanics, Heat Transfer, Fluid Mechanics Design Project Production of Ethanol Your assignment is to continue evaluating the details of a process to produce 30,000 tonne/y of ethanol from ethylene.
More informationSalt deposition in FCC gas concentration
Salt Deposition in FCC Gas Concentration Units Michel Melin Director Technical Service Grace Davison Refining Technologies Europe, Middle East and Africa Colin Baillie Marketing Manager Grace Davison Refining
More informationRaymond A. Adomaitis. March 7, 2012
Raymond A. Adomaitis March 7, 2012 To be covered: Class syllabus (http://www.isr.umd.edu/ adomaiti/ench446), grading Team selection (4 members per team) Initial project description Approximate schedule
More informationA BASIC IMMERSION FIRETUBE FLOWNEX MODEL
A BASIC IMMERSION FIRETUBE FLOWNEX MODEL This case study demonstrates the implementation of a basic immersion firetube model in Flownex and presents natural draft and forced draft examples. OIL AND GAS
More informationFluid Mechanics, Heat Transfer, Thermodynamics. Design Project. Production of Ammonia
Fluid Mechanics, Heat Transfer, Thermodynamics Design Project Production of Ammonia Your assignment is to continue evaluating the details of a process to produce 50,000 tonne/y of ammonia from a syngas
More informationSEPARATION OF OIL WATER EMULSION FROM CAR WASHES
SEPARATION OF OIL WATER EMULSION FROM CAR WASHES S. Panpanit, C. Visvanathan, and S. Muttamara. Environmental Engineering Program, Asian Institute of Technology, P.O. Box: 4, Klong Luang 12120, Pathumthani,
More informationINJEÇÃO DE CO 2 PARA PRODUÇÃO ACRESCIDA DE METANO DE CARVÃO EM CAMADA CO 2 INJECTION FOR ENHANCED COALBED METHANE (ECBM)
INJEÇÃO DE CO 2 PARA PRODUÇÃO ACRESCIDA DE METANO DE CARVÃO EM CAMADA CO 2 INJECTION FOR ENHANCED COALBED METHANE (ECBM) C.F. Rodrigues 1 & M.J. Lemos de Sousa 3 1 FPENAS, University of Fernando Pessoa,
More informationHeavy Oil and Bitumen Analytical. Understanding Their Capabilities
Heavy Oil and Bitumen Analytical Methods: Understanding Their Capabilities and dlimitationsi i Project Review & Update /COQG Meeting Calgary, Alberta June 24 th, 2008 Project Manager: Bryan Fuhr, ARC (fuhr@arc.ab.ca)
More informationA New Optimisation Based Retrofit Approach for Revamping an Egyptian Crude Oil Distillation Unit
Available online at www.sciencedirect.com ScienceDirect Energy Procedia 36 (2013 ) 454 464 TerraGreen 13 International Conference 2013  Advancements in Renewable Energy and Clean Environment A New Optimisation
More informationModelling and Simulation of Glycol Dehydration Unit of a Natural Gas Plant
International Journal of Engineering and Technology Volume 3 No. 7, July, 2013 Modelling and Simulation of Glycol Dehydration Unit of a Natural Gas Plant Akpa, Jackson Gunorubon 1, Igbagara, Princewill
More informationMembraneBased Technologies for Sustainable Production of Power
MembraneBased Technologies for Sustainable Production of Power Menachem Elimelech Department of Chemical & Environmental Engineering Yale University WaterEnergy Nexus Symposium, January 29, 213, Exhibition
More informationTwin Screw Extruder and Continuous Mixer Rate Limitations
MPC Materials Processing Consultants LLC Twin Screw Extruder and Continuous Mixer Rate Limitations Anthony C. Neubauer SPE Fellow; Dow Fellow (retired) Materials Processing Consultants LLC Why Extruders?
More informationIntegrating RiskBased Inspection Recommendations with Inspection Programs and Integrity Operating Windows
Integrating RiskBased Inspection Recommendations with Inspection Programs and Integrity Operating Windows Lynne Kaley, PE Principal Trinity Bridge, LLC Savannah, GA W. Clay White Fixed Equipment Network
More informationInfluence of Process Operations on VOC and BTEX Emissions from Glycol Dehydration Units
Page 1 of 12 Influence of Process Operations on VOC and BTEX Emissions from Glycol Dehydration Units MICHAEL W. HLAVINKA, VICENTE N. HERNANDEZVALENCIA, JERRY A. BULLIN, Bryan Research & Engineering, Inc.,
More informationJournal of Emerging Trends in Engineering and Applied Sciences (JETEAS) 4(5): (ISSN: )
Journal of Emerging Trends in Engineering and Applied Sciences (JETEAS) 4(5): 731736 Scholarlink Research Institute Journals, 2013 (ISSN: 21417016) jeteas.scholarlinkresearch.org Journal of Emerging
More informationHydrate Formation in Chevron Mabee Unit for NGL Recovery and CO 2 Purification for EOR. Abstract
Hydrate Formation in Chevron Mabee Unit for NGL Recovery and CO 2 Purification for EOR Abstract In the early 199 s, Chevron installed a new process to recover natural gas liquids (NGLs) from recycled CO
More informationCONTROL VOLUME ANALYSIS USING ENERGY. By Ertanto Vetra
CONTROL VOLUME ANALYSIS USING ENERGY 1 By Ertanto Vetra Outlines Mass Balance Energy Balance Steady State and Transient Analysis Applications 2 Conservation of mass Conservation of mass is one of the most
More informationSupporting Information
Supporting Information Influence of Natural Organic Matter Fouling and Osmotic Backwash on Pressure Retarded Osmosis Energy Production from Natural Salinity Gradients NGAI YIN YIP AND MENACHEM ELIMELECH*
More informationProblems at the Cumene Production Facility, Unit 800
Problems at the Cumene Production Facility, Unit 800 Background Cumene (isopropyl benzene) is produced by reacting propylene with benzene. During World War II, cumene was used as an octane enhancer for
More informationJ. Christopher Lewis Distillation Column Flooding Predictor INTRODUCTION
STSAIChE Energy Forum March 3, 2005 J. Christopher Lewis, UT Austin George E. Dzyacky, 2ndpoint L.L.C. 3/05 INTRODUCTION Background Technology Results Conclusions Acknowledgements BACKGROUND The Inventor
More informationGUIDANCE DOCUMENT April 6, Guidance on Estimating Condensate and Crude Oil Loading Losses from Tank Trucks
OKLAHOMA DEPARTMENT OF ENVIRONMENTAL QUALITY AIR QUALITY DIVISION GUIDANCE DOCUMENT April 6, 207 SUBJECT: Guidance on Estimating Condensate and Crude Oil Loading Losses from Tank Trucks SECTION I. INTRODUCTION
More informationModelling of post combustion capture plant flexibility
Modelling of post combustion capture plant flexibility Workshop on operating flexibility of power plants with CCS Hanne Kvamsdal London November 1112, 2009 1 Outline Background and motivation Dynamic
More informationThe Reduced Pumping Power Requirements from Increasing the Injection Well Fluid Density
GRC Transactions, Vol. 37, 2013 The Reduced Pumping Power Requirements from Increasing the Injection Well Fluid Density Benjamin M. Adams 1, Thomas H. Kuehn 1, Jimmy B. Randolph 2, and Martin O. Saar 2
More informationModeling of Transport Phenomena in Metal Foaming
Modeling of Transport Phenomena in Metal Foaming B. Chinè 1,3 and M. Monno 2,3 1 Instituto Tecnològico de Costa Rica, Costa Rica; 2 Politecnico di Milano, Italy; 3 Laboratorio MUSP, Macchine Utensili e
More informationFLEXERAMIC CERAMIC STRUCTURED PACKING SYSTEMS
CERAMIC STRUCTURED PACKING SYSTEMS Packing Systems For Heat and Mass Transfer Applications  Distillation, Absorption, Stripping, Heat Exchange, Gas Mixing, Extraction The high performance structured packing
More informationMath Matters: Dissecting Hydrometer Calculations
Math Matters: Dissecting Hydrometer Calculations By Jonathan Sirianni, Senior Laboratory Assessor 2 Posted: April 2013 In the 16th century Galileo and the Tower of Pisa made famous the fact that two objects,
More informationEvaluating the effective diffusion coefficient within the automobile catalysts
Evaluating the effective diffusion coefficient within the automobile catalysts Hironobu Ozeki, Hiroshi Yamada, Tomohiko Tagawa and aoki Takahashi 2. Chemical Engineering, agoya University, agoya, Japan
More informationChemistry of Petrochemical Processes
Chemistry of Petrochemical Processes ChE 464 Instructor: Dr. Ahmed Arafat, PhD Office: building 45 room 106 Email: akhamis@kau.edu.sa www.kau.edu.sa.akhamis files Book Chemistry of Petrochemical Processes
More informationRemoval of CO2 and H2S using Aqueous Alkanolamine Solusions
Removal of CO2 and H2S using Aqueous Alkanolamine Solusions Zare Aliabad, H., and Mirzaei, S. Abstract This work presents a theoretical investigation of the simultaneous absorption of CO 2 and H 2 S into
More informationNEW TECHNOLOGIES FOR THE USE OF WASTE ENERGY FOR DESALINATION
NEW TECHNOLOGIES FOR THE USE OF WASTE ENERGY FOR DESALINATION DESALINATION PROCESS System A System B H 2 O NaCl H 2 O + NaCl Energy Entropy of System A < Entropy of System B Energy in above equation can
More informationTwo examples of steady state simulation with HYSYS at GALPenergia Sines Refinery
Two examples of steady state simulation with HYSYS at GALPenergia Sines Refinery José Egídio Fernandes Inverno 1*, Eurico Correia 2, Pablo JiménezAsenjo 3 and Josep A. Feliu 3 1 Galpenergia, Refinaria
More informationOSMOTIC POWER FOR REMOTE COMMUNITIES IN QUEBEC. Jonathan Maisonneuve. A Thesis. In the Department. Electrical and Computer Engineering
OSMOTIC POWER FOR REMOTE COMMUNITIES IN QUEBEC Jonathan Maisonneuve A Thesis In the Department of Electrical and Computer Engineering Presented in Partial Fulfillment of the Requirements For the Degree
More informationOptimally Economic Design of Flare Systems
Optimally Economic Design of Flare Systems Hossein Shokouhmand, Shahab Hosseini Abstract Flares are one of the important parts of oil and gas refineries that burn and safely dispose purge gas. The necessity
More informationThermodynamic Performance Evaluation of a Reverse Osmosis and Nanofiltration Desalination
Thermodynamic Performance Evaluation of a Reverse Osmosis and Nanofiltration Desalination Y.Aroussy 12  M. Nachtane 1, D. Saifaoui 1 M.Tarfaoui 3 and M. Rouway 1 1 Renewable Energy Laboratory and dynamic
More informationOnLine Gas Analysis In Air Separation Plants
Application Data Sheet ADS 1032815A.A01 March, 2008 Application Data OnLine Gas Analysis In Air Separation Plants APPLICATION Emerson provides several Rosemount Analytical gas analyzer technologies to
More informationModeling of HTPEM Fuel Cell StartUp Process by Using Comsol Multiphysics
Modeling of HTPEM Fuel Cell StartUp Process by Using Comsol Multiphysics Y. Wang *1,2, J. Kowal 1,2 and D. U. Sauer 1,2,3 1 Electrochemical Energy Conversion and Storage Systems Group, Institute for Power
More information5/2/13. Zooplankton! Phytoplankton! Nutrients!
Phytoplankton! Zooplankton! Nutrients! 1 Phytoplankton! Zooplankton! Critical Depth Recycled Nutrients! Oxidized Nutrients! Detritus! Rest of Ocean Biological and Solubility Pumps 2 New (Export) vs. Regenerated
More informationAmine Plant Energy Requirements & Items impacting the SRU
Amine Plant Energy Requirements & Items impacting the SRU 10 October 2016 AGRU energy needs Amine energy requirements Regeneration Processing effects Leanness required Determine required leanness Over
More informationGAS CONDITIONING & PROCESSING TRAINING
Training Title GAS CONDITIONING & PROCESSING TRAINING Training Duration 5 days Training Venue and Dates Gas Conditioning & Processing 5 07 11 April $3,750 Dubai, UAE In any of the 5 star hotels. The exact
More informationMaterial Tested ToDate
THIN FILM EVAPORATION FOR REUSERECYCLE OF WASTE ORGANIC SOLUTIONS W. N. Whinnery  Paducah Gaseous Diffusion Plant* Paducah, Kentucky ABSTRACT A thin film evaporator TFE has been used at PGDP to evaluate
More informationAltela, Inc. Treating water naturally
Altela, Inc. Treating water naturally A Novel Solution for the Energy/Water Nexus: Lowcost Water Desalination Using Waste Heat from CSP 23 October 09 Water and Land for Renewable Energy in the Southwest
More informationEthylene Production Plant Design
Cooper Union for the Advancement of Science and Art Che 161.2: Process Evaluation and Design II Ethylene Production Plant Design Authors: Ghazal Erfani Ciera Lowe Joshua Mayourian Instructor: Professor
More informationChapter 4.1. Estimating Manure Inventory. learning objectives
Estimating Manure Inventory learning objectives Briefly explain the importance of determining manure weight or volume. Estimate the weight of solid manure in a pile. Estimate the volume of liquid manure
More informationSite Verified Contaminant Transport Model as a Mathematical Vehicle for Prevention of the Natural Aquifer Contamination
PUBLS. INST. GEOPHYS. POL. ACAD. SC., E10 (406), 2008 Site Verified Contaminant Transport Model as a Mathematical Vehicle for Prevention of the Natural Aquifer Contamination Andrzej ANISZEWSKI Szczecin
More informationCalculate the Costs of Piping System Elements
Calculate the Costs of Piping System Elements by Ray Hardee, Engineered Software, Inc. Last month s column described the process of creating an energy cost balance sheet for a piping system (see Figure
More informationQualitative Phase Behavior and Vapor Liquid Equilibrium Core
2/22/2017 Qualitative Phase Behavior and Qualitative Phase Behavior Introduction There are three different phases: solid, liquid, and gas (vapor) Energy must be added to melt a solid to form liquid If
More informationOptions for Removing Methanol from NGL in an Amine Treater Abstract. Submitted to SOGAT 2017 by:
Options for Removing Methanol from NGL in an Amine Treater Abstract Methanol is commonly injected into hydrocarbon fluids to inhibit hydrate formation. Bulk methanol removal from a hydrocarbon fluid often
More informationEnergy Balances and Numerical Methods Design Project. Production of Methyl TertiaryButyl Ether
Energy Balances and Numerical Methods Design Project Production of Methyl TertiaryButyl Ether Methyl TertiaryButyl Ether () is a gasoline additive used to increase octane number that is produced from
More informationParticle Size Determination of Porous Powders Using the SediGraph
Application Note 94 Particle Size Determination of Porous Powders Using the SediGraph Sedimentation analysis based upon Stokes Law provides a convenient method for determining particle size distribution
More informationRandom Packing. AlphaPACK DESIGN SHEET OVERVIEW
OVERVIEW Packed beds formed by dumping bulk random packing elements of consistent shape and size will provide the consistent surface and voidage characteristics necessary for predictable mass transfer
More informationAir Pollution Technology Fact Sheet
Air Pollution Technology Fact Sheet 1. Name of Technology: PackedBed/PackedTower Wet Scrubber This type of technology is a part of the group of air pollution controls collectively referred to as wet
More informationMultiphysics Modelling of Sound Absorption in Rigid Porous Media Based on Periodic Representations of Their Microstructural Geometry
Multiphysics Modelling of Sound Absorption in Rigid Porous Media Based on Periodic Representations of Their Microstructural Geometry TOMASZ G. ZIELIŃSKI Institute of Fundamental Technological Research
More informationWATER RECYCLING PLANT IN WAFRA. Feras Al Salem
WATER RECYCLING PLANT IN WAFRA Feras Al Salem Introduction 2 The Joint Operations (JO) was born in 1960 when the two oil companies formed a joint committee to oversee and supervise their operations with
More informationSimple Dew Point Control HYSYS v8.6
Simple Dew Point Control HYSYS v8.6 Steps to set up a simulation in HYSYS v8.6 to model a simple dew point control system consisting of: Gas chiller Flash separator Liquid stabilizer with gas recycle &
More informationSOFI FILTER Selfcleaning microfilter from 1 µm
SOFI FILTER Selfcleaning microfilter from 1 µm Sofi Filtration Ltd, together with the Department of Materials Science and Engineering at Aalto University of Finland, has developed a new type of dynamic
More informationPermeability, Flow Rate, and Hydraulic Conductivity Determination for Variant Pressures and Grain Size Distributions
Permeability, Flow Rate, and Hydraulic Conductivity Determination for Variant Pressures and Grain Size Distributions Nick Desiderio, npd5050@psu.edu, February 18, 2014 Abstract Carbon capture and storage
More informationImprovement of distillation column efficiency by integration with organic Rankine power generation cycle. Introduction
Improvement of distillation column efficiency by integration with organic Rankine power generation cycle Dmitriy A. Sladkovskiy, St.Petersburg State Institute of Technology (technical university), Saint
More informationNOVEL DISTILLATION CONCEPTS USING ONESHELL COLUMNS
NOVEL DISTILLATION CONCEPTS USING ONESHELL COLUMNS ärbel Kolbe, Sascha Wenzel Krupp Uhde GmbH, Dortmund, Germany ASTRACT This presentation examines the procedures involved in implementing the dividedwall
More informationUrine concentration by forward osmosis process
The 13 th IWA specialized conference on small water and wastewater systems The 5 th IWA specialized conference on resourcesoriented sanitation September 14 th ~16 th, 216 Urine concentration by forward
More informationProperties of Matter. Chemical Properties and Effects on Pollutant Fate. Characteristics of Chemical Changes. Physical Characteristics
Properties of Matter Chemical Properties and Effects on Pollutant Fate Physical Characteristics Characteristics of Chemical Changes Melting point Boiling point Vapor pressure Color State (solid, liquid,
More informationA crude oil refinery is an industrial process plant where crude oil is processed and refined into different petroleum products (i.e.
A crude oil refinery is an industrial process plant where crude oil is processed and refined into different petroleum products (i.e. gasoline, diesel, kerosene, jet fuel) This figure shows a typical refinery
More informationd&wr desalination & WATER REUSE
d&wr desalination & WATER REUSE FebruaryMarch 2013 www.desalination.biz Volume 22 Issue 4 International Desalination Association Successful year for Shuweihat S2 Very high performance ratio confirmed
More informationSample Conditioning Instruments. Jonna Kannosto Technical Marketing Specialist, PhD
Sample Conditioning Instruments Jonna Kannosto Technical Marketing Specialist, PhD Dekati Solutions: Complete setups It s not only the source or measurement instrument! It s also how to take a proper sample!
More informationAssignment I Design of a Marine Outfall
Assignment I Design of a Marine Outfall Environmental Hydraulics DESIGN OF A MARINE OUTFALL WITH A DIFFUSER FOR COOLING WATER A cooling water flow of 20 m 3 /s from a nuclear power plant should be discharged
More informationCoalbed Methane Fundamental Concepts
Coalbed Methane Fundamental Concepts By: K. Aminian Petroleum & Natural Gas Engineering Department West Virginia University Introduction This article is the first in a series of articles that will discuss
More informationDesign of Experiment. Jill Williams and Adam Krinke. Fuel Cell Project
Design of Experiment Jill Williams and Adam Krinke Fuel Cell Project Spring 2005 Introduction The Proton Exchange Membrane (PEM) fuel cell requires a relatively stringent environment for operation. The
More informationEnvironmental Technologies
Environmental Technologies Environmental Technologies Our work in environmental fields is centred on the application of mass transfer technology applied to the abatement of air and waterborne pollution.
More informationChapters 5, 6, and 7. Use T 0 = 20 C and p 0 = 100 kpa and constant specific heats unless otherwise noted. Note also that 1 bar = 100 kpa.
Chapters 5, 6, and 7 Use T 0 = 20 C and p 0 = 100 kpa and constant specific heats unless otherwise noted. Note also that 1 bar = 100 kpa. 51. Steam enters a steadyflow device at 16 MPa and 560 C with
More informationUtilization of Air Permeability In Predicting The Thermal Conductivity
ORIGINAL PAPER/PEERREVIEWED Utilization of Air Permeability In Predicting The Thermal Conductivity By Pamela BanksLee a *, Massoud Mohammadi b, Parviz Ghadimi c Abstract: General linear regression models
More informationSimulation of Binary Mixture Droplet Evaporation using VOF Methods
Peter Keller and Christian Hasse Department of Energy Process Engineering and Chemical Engineering TU Bergakademie Freiberg Simulation of Binary Mixture using VOF Methods June 14, 2011 6 th OpenFOAM R
More informationWET SCRUBBER COLUMN FOR AIR DETRITIATION
A. N. PEREVEZENTSEV* and A. C. BELL EURATOM0UKAEA Fusion Association Culham Science Centre, Abingdon OX14 3DB, United Kingdom B. M. ANDREEV, M. B. ROZENKEVICH, Yu. S. PAK, and A. V. OVCHAROV D. Mendeleev
More informationDetermination of LangmuirHinshelwood gasification kinetics from integral drop tube experiments. Florian Keller, Felix Küster, Bernd Meyer
Determination of LangmuirHinshelwood gasification kinetics from integral drop tube experiments Florian Keller, Felix Küster, Bernd Meyer 1 I. Motivation & Background II. Gasification experiments III.
More informationEnergy Balances and Numerical Methods Design Project. Production of Cumene
Process Description Energy Balances and Numerical Methods Design Project Production of Cumene Figure 1 is a preliminary process flow diagram (PFD) for the cumene production process. The raw materials are
More informationFluid Mechanics, Heat Transfer, Thermodynamics Design Project. Production of Ethylbenzene
Fluid Mechanics, Heat Transfer, Thermodynamics Design Project Production of Ethylbenzene We continue to investigate the feasibility of constructing a new, grassroots, 80,000 tonne/y, ethylbenzene facility.
More informationMulti Stage Flash Desalination with Direct Mixing Condensation
Multi Stage Flash Desalination with Direct Mixing Condensation Andrea Cipollina*, Giorgio Micale, Salvatore Noto, Alberto Brucato Dipartimento di Ingegneria Chimica Gestionale Informatica Meccanica, Università
More informationCEE 371 Water and Wastewater Systems
Updated: 22 November 2009 CEE 371 Water and Wastewater Systems Print version Lecture #19 Drinking Water Treatment: Granular Media Filtration (cont.) Reading: Chapter 7, pp.217225 David Reckhow CEE 371
More informationChapter 6. Multiphase Systems. Dr. M. A. A. Shoukat Choudhury Website:
Chapter 6 Multiphase Systems Dr. M. A. A. Shoukat Choudhury Email: shoukat@buet.ac.bd Website: http://teacher.buet.ac.bd/shoukat/ Multiphase Systems Why Study?  Phase change operations such as freezing,
More informationHideout of Sodium Phosphates in Steam Generator Crevices
Hideout of Sodium Phosphates in Steam Generator Crevices By Gwendy Harrington Department of Chemical Engineering, University of New Brunswick, P.O. Box 4400, Fredericton, New Brunswick, E3B 5A3 Abstract
More informationEfficiency improvement of steam power plants in Kuwait
Energy and Sustainability V 173 Efficiency improvement of steam power plants in Kuwait H. Hussain, M. Sebzali & B. Ameer Energy and Building Research Center, Kuwait Institute for Scientific Research, Kuwait
More information